Serving communities within a 40 mile radius of our home base in Clanton, our team is equipped to tackle your air conditioning and heating needs. Whether your system needs a minor repair, a complete overhaul, or just a maintenance check, Giles is here to get the job done as quickly and efficiently as possible.
Clanton | Prattville | Millbrook | Montgomery | Alabaster | Pelham | Montevallo | Calera | Jemison | Mineral Springs | Verbena | Marbury | Pine Level
Completed final inspection on new unit installed a few weeks ago. We complete these inspections after all installs to ensure that all work was completed to the standards expected of our company.
Found unit low of Freon and replaced a bad Schaefer valve.
Found system not running on outside because two pole contactor and run capacitor was bad.. replaced them both and checked ref and all is good at this time..
No cooling call. Found evaporator coil frozen up due to coil being dirty. Thawed unit and Washed coil. Checked operation of cooling. All is good!
Completed final inspection on a new unit where I checked all unit wiring, refrigerant levels, heating, cooling, emergency heat.
Found bad duel run capacitor bad and had the compressor not working.. changed it out and changed ref and all is good at this time!!
Found flare on the txv leaking. Re-made the flare, leak checked and got the customers unit back cooling properly.
Found and replaced a bad capacitor that was keeping the condenser fan from running.
Found that both outdoor units were not coming on. So I tested the capacitors and both were bad. Replaced both of and the house is cooling down properly.
Clanton, AL 35045